
(menu-descriptor 
   (menu-id          my-menu-id)
   (author           'Hubert Hoegl')
   (date             '2001-03-24 ')
   (ml-version       '0.1')
   (delay-reset-all  120)  
   (delay-passwd     10)                                   
   (delay-help       2)                                      
   (org-var          0x1400)
)

(menu-struct 
   (menu-id topm) 
   (menu-parent nil)
   (menu-title 'Strg.W.____')
   (menu-list 
      (menu-id zeitanzeige leaf)
      (menu-id status submenu)
      (menu-id param submenu)  
      (menu-id sensors submenu)  
      (menu-id itimer submenu)  
      (menu-id clock submenu)  
      (menu-id outputs submenu)
      (menu-id info submenu)
   )
)

(menu-struct 
   (menu-id param) 
   (menu-parent topm)
   (menu-title 'Parameter')
   (menu-list 
      (menu-id solpara submenu)  
      (menu-id bwpara submenu)  
;      (menu-id holzpara submenu)  
      (menu-id pufferpara submenu)  
      (menu-id heizpara submenu)  
      (menu-id oelpara submenu)
      (menu-id hkhauspara submenu)
      (menu-id hkmuehlepara submenu)
   )
)

(menu-struct 
   (menu-id solpara) 
   (menu-parent param)
   (menu-title 'Para.Solar')
   (menu-list 
        (menu-id parasol1 leaf) 
        (menu-id parasol2 leaf) 
        (menu-id parasol3 leaf) 
        (menu-id parasol4 leaf) 
        (menu-id parasol5 leaf) 
        (menu-id parasol10 leaf) 
        (menu-id parasol6 leaf) 
        (menu-id parasol9 leaf) 
        (menu-id parasol7 leaf) 
        (menu-id parasol8 leaf) 
   )
)

(menu-struct 
   (menu-id bwpara) 
   (menu-parent param)
   (menu-title 'Para.Bw')
   (menu-list 
        (menu-id bw1 leaf)      
        (menu-id bw2 leaf) 
        (menu-id bw3 leaf) 
        (menu-id bw4 leaf) 
   )
)

(menu-struct 
   (menu-id pufferpara) 
   (menu-parent param)
   (menu-title 'Para.Puffer')
   (menu-list 
        (menu-id puffer1 leaf)      
;        (menu-id puffer2 leaf)      
;        (menu-id puffer3 leaf)      
   )
)

(menu-struct 
   (menu-id heizpara) 
   (menu-parent param)
   (menu-title 'Para.Heiz')
   (menu-list 
        (menu-id heiz1 leaf)      
   )
)

(menu-struct 
   (menu-id oelpara) 
   (menu-parent param)
   (menu-title 'Para.Gaskessel')
   (menu-list 
        (menu-id oel1 leaf)      
;        (menu-id oel2 leaf)      
;        (menu-id oel3 leaf)      
;        (menu-id oel4 leaf)      
;        (menu-id oel5 leaf)
;        (menu-id oel6 leaf)
;        (menu-id oel7 leaf)
   )
)

(menu-struct 
   (menu-id hkhauspara) 
   (menu-parent param)
   (menu-title 'Para.HK1')
   (menu-list 
        (menu-id hkh-kp20 leaf)      
        (menu-id hkh-kp10 leaf)      
        (menu-id hkh-k0   leaf)      
        (menu-id hkh-km10 leaf)      
        (menu-id hkh-km20 leaf)      
        (menu-id hkh-absenk leaf)      
        (menu-id hkh-mte  leaf)      
        (menu-id hkh-mta  leaf)      
   )
)

(menu-struct 
   (menu-id hkmuehlepara) 
   (menu-parent param)
   (menu-title 'Para.HK2')
   (menu-list 
        (menu-id hkm-kp20 leaf)      
        (menu-id hkm-kp10 leaf)      
        (menu-id hkm-k0   leaf)      
        (menu-id hkm-km10 leaf)      
        (menu-id hkm-km20 leaf)      
        (menu-id hkm-absenk leaf)      
        (menu-id hkm-mte  leaf)      
        (menu-id hkm-mta  leaf)      
   )
)

(menu-struct 
   (menu-id itimer) 
   (menu-parent topm)
   (menu-title 'I-Timer')
   (menu-list 
        (menu-id itimer-pubw-1 leaf)      

        (menu-id itimer-sep leaf)

        (menu-id itimer-bw-1 leaf)      
        (menu-id itimer-bw-2 leaf) 
        (menu-id itimer-bw-3 leaf)

        (menu-id itimer-sep leaf)
        
        (menu-id itimer-hk1-1 leaf)      
        (menu-id itimer-hk1-2 leaf) 
        (menu-id itimer-hk1-3 leaf)

        (menu-id itimer-sep leaf)
        
        (menu-id itimer-hk2-1 leaf)      
        (menu-id itimer-hk2-2 leaf) 
        (menu-id itimer-hk2-3 leaf)
        
        (menu-id itimer-sep leaf)

        (menu-id itimer-zir-1 leaf)      
        (menu-id itimer-zir-2 leaf) 
        (menu-id itimer-zir-3 leaf)
        

   )
)

(menu-struct 
   (menu-id clock) 
   (menu-parent topm)
   (menu-title 'Uhr')
   (menu-list 
        (menu-id clock1 leaf)      
   )
)

(menu-struct 
   (menu-id sensors) 
   (menu-parent topm)
   (menu-title 'Sensoren')
   (menu-list 
        (menu-id se2 leaf)   ; Kollektor 
        (menu-id se8 leaf)   ; PU O 
        (menu-id se10 leaf)  ; PU U
        (menu-id se3 leaf)   ; BW O 
        (menu-id se4 leaf)   ; BW M
        (menu-id se5 leaf)   ; BW U
        (menu-id se13 leaf)  ; Pool
        (menu-id se6 leaf)   ; VL HK1 
        (menu-id se7 leaf)   ; VL HK2
        (menu-id se11 leaf)  ; VL Gaskessel 
        (menu-id se12 leaf)  ; RL Gaskessel
        (menu-id se1 leaf)   ; Aussen     
        (menu-id se9 leaf)   ; PU M 
        (menu-id se14 leaf)  ; nc 
        (menu-id se15 leaf)  ; nc
        (menu-id se16 leaf)  ; nc
   )
)

(menu-struct 
   (menu-id outputs) 
   (menu-parent topm)
   (menu-title 'Ausgaenge')
   (menu-list 
        (menu-id op1 leaf) 
        (menu-id op2 leaf)    
        (menu-id op3 leaf)   
        (menu-id op4 leaf)   
   )
)

(menu-struct 
   (menu-id status) 
   (menu-parent topm)
   (menu-title 'Status')
   (menu-list 
	(menu-id status-hz submenu)
	(menu-id status-can submenu)
	(menu-id status-debug submenu)
   )
)

(menu-struct 
   (menu-id status-hz) 
   (menu-parent status)
   (menu-title 'Status.Hz')
   (menu-list 
        (menu-id status-hz-1 leaf) 
        (menu-id status-hz-2 leaf) 
        (menu-id status-hz-3 leaf) 
        (menu-id status-hz-4 leaf) 
        (menu-id status-hz-5 leaf)
        (menu-id status-hz-6 leaf)
        (menu-id status-hz-7 leaf)
        (menu-id status-hz-8 leaf)
   )
)

(menu-struct 
   (menu-id status-can) 
   (menu-parent status)
   (menu-title 'Status.CAN')
   (menu-list 
        (menu-id status-can-1 leaf)      
        (menu-id status-can-2 leaf) 
   )
)

(menu-struct 
   (menu-id status-debug) 
   (menu-parent status)
   (menu-title 'Status.Debug')
   (menu-list 
        (menu-id status-debug-1 leaf)      
        (menu-id status-debug-2 leaf)      
        (menu-id status-debug-3 leaf)      
   )
)

(menu-struct 
   (menu-id info) 
   (menu-parent topm)
   (menu-title 'Info')
   (menu-list 
        (menu-id info1 leaf) 
        (menu-id info2 leaf)    
        (menu-id info3 leaf)    
   )
)

; -----------------------------------------------------------------------

(menu-line 
   (menu-id zeitanzeige )
   (format 
      (option 
	    (blink    off)
	    (nopts    7)
	    (opts     'So' 'Mo' 'Di' 'Mi' 'Do' 'Fr' 'Sa' )
            (default  4)  ; 1.1.1970 was a Thursday
	    (access   ro)
	    (update   0)
            (var      'm_zeit_wday')
      )
      (hfill 1)
      (date
	    (blink    off)
            (type     short)
	    (access   ro)
	    (update   0)
	    (default  '70-01-01')  ; yy-mm-dd
	    (var      'm_date')
      )
      (hfill 1)
      (time
	    (blink    off)
	    (type     short)     
            (access   ro)
	    (update   0)
	    (default  '00:00')
            (var      'm_zeit')
      )
   )
)

(menu-line 
   (menu-id param )
   (format
         (string 
	    (blink    off)
	    (value    'Parameter... ')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id solpara )
   (format
         (string 
	    (blink    off)
	    (value    'Solar... ')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id bwpara )
   (format
         (string 
	    (blink    off)
	    (value    'Brauchwasser... ')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id pufferpara )
   (format
         (string 
	    (blink    off)
	    (value    'Puffer... ')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id heizpara )
   (format
         (string 
	    (blink    off)
	    (value    'Heizung... ')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id oelpara )
   (format
         (string 
	    (blink    off)
            (value    'Gas-Kessel... ')
	    (access   ro)
	    (update   0)
	 ) 
   )
)


(menu-line 
   (menu-id hkhauspara )
   (format
         (string 
	    (blink    off)
            (value    'HK1... ')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id hkmuehlepara )
   (format
         (string 
	    (blink    off)
            (value    'HK2... ')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id itimer )
   (format
         (string 
	    (blink    off)
	    (value    'I-Timer... ')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id clock )
   (format
         (string 
	    (blink    off)
	    (value    'Uhr... ')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id sensors )
   (format
         (string 
	    (blink    off)
	    (value    'Sensoren... ')
	    (access   ro)
	    (update   0)
	 ) 
   )        
)

(menu-line 
   (menu-id outputs )
   (format
         (string 
	    (blink    off)
	    (value    'Ausgaenge... ')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id status )
   (format
         (string 
	    (blink    off)
	    (value    'Status... ')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id status-hz )
   (format
         (string 
	    (blink    off)
	    (value    'Heizung... ')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id status-can )
   (format
         (string 
	    (blink    off)
	    (value    'CAN... ')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id status-debug )
   (format
         (string 
	    (blink    off)
	    (value    'Debug... ')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id info )
   (format
         (string 
	    (blink    off)
	    (value    'Info... ')
	    (access   ro)
	    (update   0)
	 ) 
   )
)


(menu-line 
   (menu-id parasol1 )
   (format
         (string 
	    (blink    off)
            (value    'df_sol_bw_e')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       30)
	    (step     1)
	    (default  8)
	    (access   rw)
	    (update   0)
	    (var      'menu_df_sol_bw_e')
	 )
   )
)

(menu-line 
   (menu-id parasol2 )
   (format
         (string 
	    (blink    off)
            (value    'df_sol_bw_a')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       30)
	    (step     1)
	    (default  4)
	    (access   rw)
	    (update   0)
	    (var      'menu_df_sol_bw_a')
	 )
   )
)

(menu-line 
   (menu-id parasol3 )
   (format
         (string 
	    (blink    off)
            (value    'df_sol_po_e')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       30)
	    (step     1)
	    (default  8)
	    (access   rw)
	    (update   0)
	    (var      'menu_df_sol_pu_e')
	 )
   )
)

(menu-line 
   (menu-id parasol4 )
   (format
         (string 
	    (blink    off)
            (value    'df_sol_po_a')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       30)
	    (step     1)
	    (default  8)
	    (access   rw)
	    (update   0)
	    (var      'menu_df_sol_pu_a')
	 )
   )
)

(menu-line 
   (menu-id parasol5 )
   (format
         (string 
	    (blink    off)
            (value    'sw_sol_bw_max')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     30)
	    (to       90)
	    (step     1)
	    (default  60)
	    (access   rw)
	    (update   0)
	    (var      'menu_sw_sol_bw_max')
	 )
   )
)

(menu-line 
   (menu-id parasol6 )
   (format
         (string 
	    (blink    off)
	    (value    'sw_kol_min')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       30)
	    (step     1)
	    (default  30)
	    (access   rw)
	    (update   0)
	    (var      'menu_sw_kol_min')
	 )
   )
)

(menu-line 
   (menu-id parasol7 )
   (format
         (string 
	    (blink    off)
            (value    'ti_lauf [min]')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     1)
	    (to       60)
	    (step     1)
	    (default  10)
	    (access   rw)
	    (update   0)
	    (var      'menu_ti_umsch')
	 )
   )
)

(menu-line 
   (menu-id parasol8 )
   (format
         (string 
	    (blink    off)
	    (value    'ti_stop [min]')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     1)
	    (to       15)
	    (step     1)
	    (default  2)
	    (access   rw)
	    (update   0)
	    (var      'menu_ti_stop')
	 )
   )
)

(menu-line 
   (menu-id parasol9 )
   (format
         (string 
	    (blink    off)
	    (value    'sw_kol_max')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     80)
	    (to       120)
	    (step     1)
	    (default  90)
	    (access   rw)
	    (update   0)
	    (var      'menu_sw_kol_max')
	 )
   )
)

(menu-line 
   (menu-id parasol10 )
   (format
         (string 
	    (blink    off)
            (value    'sw_pool_max')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
            (from     0)
            (to       50)
	    (step     1)
            (default  10)
	    (access   rw)
	    (update   0)
            (var      'menu_sw_pool_max')
	 )
   )
)

; Minimale BW-Temperatur fuer Oelkesselfreigabe
(menu-line 
   (menu-id bw1 )
   (format
         (string 
	    (blink    off)
	    (value    'sw_bw_min')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       50)
	    (step     1)
	    (default  15)
	    (access   rw)
	    (update   0)
	    (var      'menu_sw_bw_min')
	 )
   )
)

(menu-line 
   (menu-id bw2 )
   (format
         (string 
	    (blink    off)
	    (value    'sw_bw_max')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       70)
	    (step     1)
	    (default  15)
	    (access   rw)
	    (update   0)
	    (var      'menu_sw_bw_max')
	 )
   )
)

(menu-line 
   (menu-id bw3 )
   (format
         (string 
	    (blink    off)
            (value    'df_pu_bw_e')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       70)
	    (step     1)
	    (default  15)
	    (access   rw)
	    (update   0)
            (var      'menu_df_pu_bw_e')
	 )
   )
)

(menu-line 
   (menu-id bw4 )
   (format
         (string 
	    (blink    off)
            (value    'df_pu_bw_a')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       70)
	    (step     1)
	    (default  15)
	    (access   rw)
	    (update   0)
            (var      'menu_df_pu_bw_a')
	 )
   )
)

(menu-line 
   (menu-id oel1 )
   (format
         (string 
	    (blink    off)
            (value    'Gas-K.Ueberst.')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       30)
	    (step     1)
	    (default  15)
	    (access   rw)
	    (update   0)
            (var      'menu_param_oel_uebersteuerung')
	 )
   )
)

;(menu-line 
;   (menu-id oel2 )
;   (format
;         (string 
;            (blink    off)
;            (value    'sw_gaskessel_vl')
;            (access   ro)
;            (update   0)
;         ) 
;         (hfill 0)     
;         (counter
;            (blink    off)
;            (from     0)
;            (to       60)
;            (step     1)
;            (default  30)
;            (access   rw)
;            (update   0)
;            (var      'menu_sw_bhkw_vl')
;         )
;   )
;)

;(menu-line 
;   (menu-id oel3 )
;   (format
;         (string 
;            (blink    off)
;            (value    'sw_gaskessel_rl')
;            (access   ro)
;            (update   0)
;         ) 
;         (hfill 0)     
;         (counter
;            (blink    off)
;            (from     0)
;            (to       60)
;            (step     1)
;            (default  30)
;            (access   rw)
;            (update   0)
;            (var      'menu_sw_bhkw_rl')
;         )
;   )
;)
;
;(menu-line
;   (menu-id oel4)
;   (format
;         (string 
;            (blink    off)
;            (value    'mi_rl_te')
;            (access   ro)
;            (update   0)
;         ) 
;         (hfill 0)     
;         (counter
;            (blink    off)
;            (from     1)
;            (to       300)
;            (step     1)
;            (default  5)
;            (access   rw)
;            (update   0)
;            (var      'menu_pu_misch_te')
;         )
;   )
;)

;(menu-line
;   (menu-id oel5)
;   (format
;         (string 
;            (blink    off)
;            (value    'mi_rl_ta')
;            (access   ro)
;            (update   0)
;        ) 
;        (hfill 0)     
;        (counter
;           (blink    off)
;           (from     5)
;           (to       300)
;           (step     1)
;           (default  5)
;           (access   rw)
;            (update   0)
;            (var      'menu_pu_misch_ta')
;         )
;   )
;)

;(menu-line 
;   (menu-id oel6 )
;   (format
;         (string 
;            (blink    off)
;            (value    'df_bhkw_bw_e')
;            (access   ro)
;            (update   0)
;         ) 
;         (hfill 0)     
;         (counter
;            (blink    off)
;            (from     0)
;            (to       30)
;            (step     1)
;            (default  15)
;            (access   rw)
;            (update   0)
;            (var      'menu_df_bhkw_bw_e')
;         )
;   )
;)

;(menu-line 
;   (menu-id oel7 )
;   (format
;         (string 
;            (blink    off)
;            (value    'df_bhkw_bw_a')
;            (access   ro)
;            (update   0)
;         ) 
;         (hfill 0)     
;         (counter
;            (blink    off)
;            (from     0)
;            (to       30)
;            (step     1)
;            (default  15)
;            (access   rw)
;            (update   0)
;            (var      'menu_df_bhkw_bw_a')
;         )
;   )
;)

(menu-line
   (menu-id hkh-kp20)
   (format
         (string 
	    (blink    off)
	    (value    'Kennlinie +20')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       70)
	    (step     1)
	    (default  15)
	    (access   rw)
	    (update   0)
	    (var      'menu_hkh_kp20')
	 )
   )
)

(menu-line
   (menu-id hkh-kp10)
   (format
         (string 
	    (blink    off)
	    (value    'Kennlinie +10')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       70)
	    (step     1)
	    (default  15)
	    (access   rw)
	    (update   0)
	    (var      'menu_hkh_kp10')
	 )
   )
)

(menu-line
   (menu-id hkh-k0)
   (format
         (string 
	    (blink    off)
	    (value    'Kennlinie 0')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       70)
	    (step     1)
	    (default  15)
	    (access   rw)
	    (update   0)
	    (var      'menu_hkh_k0')
	 )
   )
)

(menu-line
   (menu-id hkh-km10)
   (format
         (string 
	    (blink    off)
	    (value    'Kennlinie -10')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       70)
	    (step     1)
	    (default  15)
	    (access   rw)
	    (update   0)
	    (var      'menu_hkh_m10')
	 )
   )
)

(menu-line
   (menu-id hkh-km20)
   (format
         (string 
	    (blink    off)
	    (value    'Kennlinie -20')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       70)
	    (step     1)
	    (default  15)
	    (access   rw)
	    (update   0)
	    (var      'menu_hkh_m20')
	 )
   )
)

(menu-line
   (menu-id hkh-absenk)
   (format
         (string 
	    (blink    off)
	    (value    'Absenkung')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       50)
	    (step     1)
	    (default  15)
	    (access   rw)
	    (update   0)
	    (var      'menu_hkh_absenk')
	 )
   )
)

(menu-line
   (menu-id hkh-mte)
   (format
         (string 
	    (blink    off)
	    (value    'misch_te:')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
            (from     1)
	    (to       300)
	    (step     1)
	    (default  5)
	    (access   rw)
	    (update   0)
	    (var      'menu_hkh_misch_te')
	 )
   )
)

(menu-line
   (menu-id hkh-mta)
   (format
         (string 
	    (blink    off)
	    (value    'misch_ta:')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     5)
	    (to       300)
	    (step     1)
	    (default  5)
	    (access   rw)
	    (update   0)
	    (var      'menu_hkh_misch_ta')
	 )
   )
)




(menu-line
   (menu-id hkm-kp20)
   (format
         (string 
	    (blink    off)
	    (value    'Kennlinie +20')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       70)
	    (step     1)
	    (default  15)
	    (access   rw)
	    (update   0)
	    (var      'menu_hke_kp20')
	 )
   )
)

(menu-line
   (menu-id hkm-kp10)
   (format
         (string 
	    (blink    off)
	    (value    'Kennlinie +10')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       70)
	    (step     1)
	    (default  15)
	    (access   rw)
	    (update   0)
	    (var      'menu_hke_kp10')
	 )
   )
)

(menu-line
   (menu-id hkm-k0)
   (format
         (string 
	    (blink    off)
	    (value    'Kennlinie 0')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       70)
	    (step     1)
	    (default  15)
	    (access   rw)
	    (update   0)
	    (var      'menu_hke_k0')
	 )
   )
)

(menu-line
   (menu-id hkm-km10)
   (format
         (string 
	    (blink    off)
	    (value    'Kennlinie -10')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       70)
	    (step     1)
	    (default  15)
	    (access   rw)
	    (update   0)
	    (var      'menu_hke_m10')
	 )
   )
)

(menu-line
   (menu-id hkm-km20)
   (format
         (string 
	    (blink    off)
	    (value    'Kennlinie -20')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       70)
	    (step     1)
	    (default  15)
	    (access   rw)
	    (update   0)
	    (var      'menu_hke_m20')
	 )
   )
)

(menu-line
   (menu-id hkm-absenk)
   (format
         (string 
	    (blink    off)
            (value    'Festw.Sommer')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       50)
	    (step     1)
            (default  25)
	    (access   rw)
	    (update   0)
	    (var      'menu_hke_absenk')
	 )
   )
)

(menu-line
   (menu-id hkm-mte)
   (format
         (string 
	    (blink    off)
	    (value    'misch_te:')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
            (from     1)
	    (to       300)
	    (step     1)
	    (default  5)
	    (access   rw)
	    (update   0)
	    (var      'menu_hke_misch_te')
	 )
   )
)

(menu-line
   (menu-id hkm-mta)
   (format
         (string 
	    (blink    off)
	    (value    'misch_ta:')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     5)
	    (to       300)
	    (step     1)
	    (default  5)
	    (access   rw)
	    (update   0)
	    (var      'menu_hke_misch_ta')
	 )
   )
)




(menu-line 
   (menu-id puffer1 )
   (format
         (string 
	    (blink    off)
	    (value    'sw_puff_entl')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     20)
	    (to       60)
	    (step     1)
	    (default  40)
	    (access   rw)
	    (update   0)
	    (var      'menu_sw_puff_entl')
	 )
   )
)

(menu-line 
   (menu-id heiz1 )
   (format
         (string 
	    (blink    off)
	    (value    'sw_sommer')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
	 (counter
            (blink    off)
	    (from     0)
	    (to       30)
	    (step     1)
	    (default  15)
	    (access   rw)
	    (update   0)
	    (var      'menu_sw_sommer')
	 )
   )
)

(menu-line 
   (menu-id clock1 )
   (format 
      (option 
	    (blink    off)
	    (nopts    7)
	    (opts     'So' 'Mo' 'Di' 'Mi' 'Do' 'Fr' 'Sa' )
            (default  5)
	    (access   rw)
	    (update   0)
            (var      'm_setclock_wday')
      )
      (hfill 1)
      (date
	    (blink    off)
            (type     short)
	    (access   rw)
	    (update   0)
	    (default  '28-09-01')  ; will be displayed as 01-09-28
	    (var      'm_setclock_date')
      )
      (hfill 1)
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '06:15')
            (var      'm_setclock_zeit')
      )
   )
)

(menu-line 
   (menu-id itimer-pubw-1 )
   (format 
      (string 
	    (blink    off)
            (value    'F P-BW ')
	    (access   ro)
            (update   0)
      )
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twpubw1b')
      )
      (hfill 1)
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twpubw1e')
      )
   )
)


(menu-line 
   (menu-id itimer-hk1-1 )
   (format 
      (string 
	    (blink    off)
            (value    'A HK1  ')
	    (access   ro)
            (update   0)
      )
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twhkh1b')
      )
      (hfill 1)
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twhkh1e')
      )
   )
)

(menu-line 
   (menu-id itimer-hk1-2 )
   (format 
      (string 
	    (blink    off)
            (value    'A HK1  ')
	    (access   ro)
            (update   0)
      )
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twhkh2b')
      )
      (hfill 1)
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twhkh2e')
      )
   )
)

(menu-line 
   (menu-id itimer-hk1-3 )
   (format 
      (string 
	    (blink    off)
            (value    'A HK1  ')
	    (access   ro)
            (update   0)
      )
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twhkh3b')
      )
      (hfill 1)
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twhkh3e')
      )
   )
)


(menu-line 
   (menu-id itimer-hk2-1 )
   (format 
      (string 
	    (blink    off)
            (value    'A HK2  ')
	    (access   ro)
            (update   0)
      )
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
	    (var      'm_twhk21b')
      )
      (hfill 1)
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
	    (var      'm_twhk21e')
      )
   )
)

(menu-line 
   (menu-id itimer-hk2-2 )
   (format 
      (string 
	    (blink    off)
            (value    'A HK2  ')
	    (access   ro)
            (update   0)
      )
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
	    (var      'm_twhk22b')
      )
      (hfill 1)
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
	    (var      'm_twhk22e')
      )
   )
)

(menu-line 
   (menu-id itimer-hk2-3 )
   (format 
      (string 
	    (blink    off)
            (value    'A HK2  ')
	    (access   ro)
            (update   0)
      )
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
	    (var      'm_twhk23b')
      )
      (hfill 1)
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
	    (var      'm_twhk23e')
      )
   )
)


(menu-line 
   (menu-id itimer-bw-1 )
   (format 
      (string 
	    (blink    off)
            (value    'S BWL  ')
	    (access   ro)
            (update   0)
      )
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twbw1b')
      )
      (hfill 1)
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twbw1e')
      )
   )
)

(menu-line 
   (menu-id itimer-bw-2 )
   (format 
      (string 
	    (blink    off)
            (value    'S BWL  ')
	    (access   ro)
            (update   0)
      )
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twbw2b')
      )
      (hfill 1)
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twbw2e')
      )
   )
)

(menu-line 
   (menu-id itimer-bw-3 )
   (format 
      (string 
	    (blink    off)
            (value    'S BWL  ')
	    (access   ro)
            (update   0)
      )
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twbw3b')
      )
      (hfill 1)
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twbw3e')
      )
   )
)

(menu-line 
   (menu-id itimer-zir-1 )
   (format 
      (string 
	    (blink    off)
            (value    'ZIRK-1 ')
	    (access   ro)
            (update   0)
      )
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twzir1b')
      )
      (hfill 1)
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twzir1e')
      )
   )
)

(menu-line 
   (menu-id itimer-zir-2 )
   (format 
      (string 
	    (blink    off)
            (value    'ZIRK-2 ')
	    (access   ro)
            (update   0)
      )
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twzir2b')
      )
      (hfill 1)
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twzir2e')
      )
   )
)

(menu-line 
   (menu-id itimer-zir-3 )
   (format 
      (string 
	    (blink    off)
            (value    'ZIRK-3 ')
	    (access   ro)
            (update   0)
      )
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twzir3b')
      )
      (hfill 1)
      (time
	    (blink    off)
	    (type     short)     
            (access   rw)
	    (update   0)
	    (default  '00:00')
            (var      'm_twzir3e')
      )
   )
)

(menu-line 
   (menu-id itimer-sep )
   (format 
      (string 
	    (blink    off)
	    (value    '----------------')
	    (access   ro)
            (update   0)
      )
   )
)

(menu-line 
   (menu-id se1 )
   (format
         (string 
	    (blink    off)
            (value    'Aussentemp.')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     SDDD)
            (access   ro)
	    (update   3)
	    (default  0)
            (var      'menu_temp_aussen')
	 )
         (string 
	    (blink    off)
	    (value    '\xdfC')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id se2 )
   (format
         (string 
	    (blink    off)
            (value    'Kollektor')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     SDDD)     
            (access   ro)
	    (update   3)
	    (default  20)
            (var      'menu_temp_solar')
	 )
         (string 
	    (blink    off)
	    (value    '\xdfC')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id se3 )
   (format
         (string 
	    (blink    off)
            (value    'BW Oben')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     SDDD)     
            (access   ro)
	    (update   3)
	    (default  20)
            (var      'menu_temp_bw_o')
	 )
         (string 
	    (blink    off)
	    (value    '\xdfC')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id se4 )
   (format
         (string 
	    (blink    off)
            (value    'BW Mitte')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     SDDD)     
            (access   ro)
	    (update   3)
	    (default  20)
            (var      'menu_temp_bw_m')
	 )
         (string 
	    (blink    off)
	    (value    '\xdfC')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id se5 )
   (format
         (string 
	    (blink    off)
            (value    'BW unten')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     SDDD)     
            (access   ro)
	    (update   3)
	    (default  20)
            (var      'menu_temp_bw_u')
	 )
         (string 
	    (blink    off)
            

	    (value    '\xdfC')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id se6 )
   (format
         (string 
	    (blink    off)
            (value    'HK1 Vorl.')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     SDDD)     
            (access   ro)
	    (update   3)
	    (default  20)
            (var      'menu_temp_hk1')
	 )
         (string 
	    (blink    off)
	    (value    '\xdfC')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id se7 )
   (format
         (string 
	    (blink    off)
            (value    'HK2 Vorl.')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     SDDD)     
            (access   ro)
	    (update   3)
	    (default  20)
            (var      'menu_temp_hk2')
	 )
         (string 
	    (blink    off)
	    (value    '\xdfC')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id se8 )
   (format
         (string 
	    (blink    off)
            (value    'PU Oben')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     SDDD)     
            (access   ro)
	    (update   3)
	    (default  20)
            (var      'menu_temp_pu1o')
	 )
         (string 
	    (blink    off)
	    (value    '\xdfC')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id se9 )
   (format
         (string 
	    (blink    off)
            (value    'PU Mitte')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     SDDD)     
            (access   ro)
	    (update   3)
	    (default  20)
            (var      'menu_temp_pu1m')
	 )
         (string 
	    (blink    off)
	    (value    '\xdfC')
	    (access   ro)
	    (update   0)
	 ) 
   )
)


(menu-line 
   (menu-id se10 )
   (format
         (string 
	    (blink    off)
            (value    'PU Unten')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     SDDD)     
            (access   ro)
	    (update   3)
	    (default  20)
            (var      'menu_temp_pu1u')
	 )
         (string 
	    (blink    off)
	    (value    '\xdfC')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id se11 )
   (format
         (string 
	    (blink    off)
            (value    'GasK.Vorl.')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     SDDD)     
            (access   ro)
	    (update   3)
	    (default  0)
            (var      'menu_temp_gas_vl')
	 )
         (string 
	    (blink    off)
	    (value    '\xdfC')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id se12 )
   (format
         (string 
	    (blink    off)
            (value    'GasK.Rueck.')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     SDDD)     
            (access   ro)
	    (update   3)
	    (default  20)
            (var      'menu_temp_gas_rl')
	 )
         (string 
	    (blink    off)
	    (value    '\xdfC')
	    (access   ro)
	    (update   0)
	 ) 
   )
)


(menu-line 
   (menu-id se13 )
   (format
         (string 
	    (blink    off)
            (value    'Pooltemp.')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     SDDD)     
            (access   ro)
	    (update   3)
	    (default  20)
            (var      'menu_temp_s12')
	 )
         (string 
	    (blink    off)
	    (value    '\xdfC')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id se14 )
   (format
         (string 
	    (blink    off)
            (value    'nc')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     SDDD)     
            (access   ro)
	    (update   3)
	    (default  20)
            (var      'menu_temp_s13')
	 )
         (string 
	    (blink    off)
	    (value    '\xdfC')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id se15 )
   (format
         (string 
	    (blink    off)
	    (value    'nc')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     SDDD)     
            (access   ro)
	    (update   3)
	    (default  20)
            (var      'menu_temp_s14')
	 )
         (string 
	    (blink    off)
	    (value    '\xdfC')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id se16 )
   (format
         (string 
	    (blink    off)
	    (value    'nc')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     SDDD)     
            (access   ro)
	    (update   3)
	    (default  0)
            (var      'menu_temp_s15')
	 )
         (string 
	    (blink    off)
	    (value    '\xdfC')
	    (access   ro)
	    (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id op1 )
   (format
         (string 
	       (blink    off)
	       (value    'K01-K08')
	       (access   ro)
	       (update   0)
	 ) 
         (hfill 0)     
	 (switch 
	       (blink    off)
	       (nswitch  8) 
	       (swinfo  '1' '2' '3' '4' '5' '6' '7' '8' )
	       (on-char  '1')
	       (off-char '_')
	       (default  '________')
	       (update   0)
	       (access   ro)
	       (var      'menu_p1') 
	 )
   )
)

(menu-line 
   (menu-id op2 )
   (format
         (string 
	       (blink    off)
	       (value    'K09-K16')
	       (access   ro)
	       (update   0)
	 ) 
         (hfill 0)     
	 (switch 
	       (blink    off)
	       (nswitch  8) 
	       (swinfo  '9' '10' '11' '12' '13' '14' '15' '16' )
	       (on-char  '1')
	       (off-char '_')
	       (default  '________')
	       (update   0)
	       (access   ro)
	       (var      'menu_p2') 
	 )
   )
)

(menu-line 
   (menu-id op3 )
   (format
         (string 
	       (blink    off)
	       (value    'K17-K24')
	       (access   ro)
	       (update   0)
	 ) 
         (hfill 0)     
	 (switch 
	       (blink    off)
	       (nswitch  8) 
	       (swinfo  '17' '18' '19' '20' '21' '22' '23' '24' )
	       (on-char  '1')
	       (off-char '_')
	       (default  '________')
	       (update   0)
	       (access   ro)
	       (var      'menu_p3') 
	 )
   )
)

(menu-line 
   (menu-id op4 )
   (format
         (string 
	       (blink    off)
	       (value    'K25-K32')
	       (access   ro)
	       (update   0)
	 ) 
         (hfill 0)     
	 (switch 
	       (blink    off)
	       (nswitch  8) 
	       (swinfo  '25' '26' '27' '28' '29' '30' '31' '32' )
	       (on-char  '1')
	       (off-char '_')
	       (default  '________')
	       (update   0)
	       (access   ro)
	       (var      'menu_p4') 
	 )
   )
)

(menu-line 
   (menu-id status-hz-1 )
   (format
         (string 
	    (blink    off)
	    (value    'Betrieb:')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (option 
	    (blink    off)
	    (nopts    2)
	    (opts     'Winter' 'Sommer')
            (default  0)
	    (access   ro)
	    (update   3)
            (var      'menu_status_betrieb')
         )
   )
)
(menu-line 
   (menu-id status-hz-2 )
   (format
         (string 
	    (blink    off)
	    (value    'Puffer1:')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (option 
	    (blink    off)
	    (nopts    2)
            (opts     ' leer' ' voll')
            (default  0)
	    (access   ro)
	    (update   3)
            (var      'menu_status_puffer1')
         )
   )
)

(menu-line 
   (menu-id status-hz-3 )
   (format
         (string 
	    (blink    off)
            (value    'BHKW.Soll')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     SDDD)
            (access   ro)
	    (update   3)
	    (default  0)
            (var      'menu_oelkessel_soll')
	 )
   )
)


(menu-line 
   (menu-id status-hz-4 )
   (format
         (string 
	    (blink    off)
            (value    'Vor.Soll HK1')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     DDD)
            (access   ro)
	    (update   3)
	    (default  0)
            (var      'menu_vorsollhaus')
	 )
   )
)

(menu-line 
   (menu-id status-hz-5 )
   (format
         (string 
	    (blink    off)
            (value    'Vor.Soll HK2')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     DDD)
            (access   ro)
	    (update   3)
	    (default  0)
            (var      'menu_vorsollmuehle')
	 )
   )
)
(menu-line 
   (menu-id status-hz-6 )
   (format
         (string 
            (blink    off)
            (value    'HZ-Quelle')
            (access   ro)
            (update   0)
         ) 
         (hfill 0)     
         (option 
            (blink    off)
            (nopts    5)
            (opts     '  Aus' 'Gas-K' ' Holz' '  Pu1' '  Pu2')
            (default  0)
            (access   ro)
            (update   0)
            (var      'menu_hz_quelle')
         )
   )
)

(menu-line 
   (menu-id status-hz-7 )
   (format
         (string 
            (blink    off)
            (value    'BW-Quelle:')
            (access   ro)
            (update   0)
         ) 
         (hfill 0)     
         (option 
            (blink    off)
            (nopts    6)
            (opts     ' Holz' '  Pu1' '  Pu2' '  Pu3' 'Gas-K' 'K.Anf')
            (default  0)
            (access   ro)
            (update   3)
            (var      'menu_status_quelle')
         )
   )
)

(menu-line 
   (menu-id status-hz-8 )
   (format
         (string 
	    (blink    off)
            (value    'BW-GAS-K.:')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (option 
	    (blink    off)
	    (nopts    2)
            (opts     'sperr' ' frei')
            (default  0)
	    (access   ro)
	    (update   3)
            (var      'menu_status_oelkessel')
         )
   )
)


(menu-line 
   (menu-id status-can-1)
   (format
         (string 
	    (blink    off)
	    (value    '#crsy_err:')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     DDDD)
            (access   ro)
	    (update   3)
	    (default  0)
            (var      'menu_can_resy_err')
	 )
   )
)

(menu-line 
   (menu-id status-can-2)
   (format
         (string 
	    (blink    off)
	    (value    '#crsy_ok:')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     DDDD)
            (access   ro)
	    (update   3)
	    (default  0)
            (var      'menu_can_resy_ok')
	 )
   )
)

(menu-line 
   (menu-id status-debug-1 )
   (format
         (string 
	    (blink    off)
	    (value    'errno:')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     DDDD)
            (access   ro)
	    (update   3)
	    (default  0)
            (var      'menu_errno')
	 )
   )
)

(menu-line 
   (menu-id status-debug-2)
   (format
         (string 
	    (blink    off)
	    (value    'n_reset:')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     DDDD)
            (access   ro)
	    (update   3)
	    (default  0)
            (var      'menu_rstcnt')
	 )
   )
)


(menu-line 
   (menu-id status-debug-3 )
   (format
         (string 
	    (blink    off)
	    (value    'Debug:')
	    (access   ro)
	    (update   0)
	 ) 
         (hfill 0)     
         (integer 
	    (blink    off)
	    (type     DDDD)
            (access   ro)
	    (update   3)
	    (default  0)
            (var      'menu_debug')
	 )
   )
)


(menu-line 
   (menu-id info1 )
   (format
         (string 
	       (blink    off)
               (value    'XXX 1.1 080931')
	       (access   ro)
	       (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id info2 )
   (format
         (string 
	       (blink    off)
               (value    '(c) 2007 B&H Hoegl')
	       (access   ro)
	       (update   0)
	 ) 
   )
)

(menu-line 
   (menu-id info3 )
   (format
         (string 
	       (blink    off)
	       (value    '    www.hhoegl.com')
	       (access   ro)
	       (update   0)
	 ) 
   )
)

;   vim:syntax=lisp
